Category:1021 Bituminous-Coated Corrugated Metal Culvert Pipe and Pipe-Arches
|Approved and Pre-Qualified List|
|QC/QA Qualified Plants for Bituminous-Coated Corrugated Metal Culvert Pipe and Pipe-Arches|
This article establishes procedures for inspecting, acceptance and reporting of bituminous-coated corrugated metal culvert pipe and pipe arches. Refer to Sec 1021 for MoDOT’s specifications.
- 1 1021.1 Apparatus
- 2 1021.2 Procedure
- 3 1021.3 Sample Record
- 4 1021.4 Laboratory Testing Guidelines for Sec 1021
(a) Micrometer capable of measuring to 0.0001 in. (0.00254 mm) and accurate to within at least 0.001 in. (0.0254 mm).
(b) Rule with suitable gradations to accurately measure the material to be inspected.
1021.2.1 Bituminous-Coated Corrugated Metal Culvert Pipe
Bituminous-coated corrugated metal culvert pipe and pipe arches are to be accepted in accordance with Sec 1021.2. The basis of acceptance for the bituminous material will be in accordance with AASHTO M 190, except acceptance may be based on samples obtained from storage or from the dipping tanks.
1021.2.3 Identification Markings
Pipe is to be marked as described in 1020.2.3 Identification Markings for Steel Sheet.
1021.2.4 Random Sampling
Random samples of steel sheet are to be taken as described in 1020.2.4 Random Sampling of Steel Sheet. Random samples of bituminous coating are to be taken in accordance with AASHTO M 190.
1021.2.5 Field Inspection
Field inspection shall be performed in accordance with and at the frequency specified in 1020.2.5 Field Inspection.
Fabrication of bituminous-coated corrugated metal culvert pipe and pipe arches shall be in accordance with Sec 1020 and AASHTO M 190.
1021.2.7 Lift Hooks or Loops
Lift hooks or loops, if agreed upon by the engineer and manufacturer, may be attached to pipe and pipe arches to facilitate handling.
1021.2.8 Repair of Damaged Bituminous Coating
Bituminous coating damaged or displaced during delivery or installation shall be repaired as directed the engineer by application of hot bituminous material of the same type as that originally used. Care shall be taken to avoid damage to the bituminous materials during heating.
1021.3 Sample Record
Sample IDs shall be assigned and sample records shall be created in accordance with 1020.3 Sample Record.
1021.4 Laboratory Testing Guidelines for Sec 1021
This article To establish procedures for Laboratory testing and reporting samples of bituminous material for coating corrugated metal culvert pipe and pipe-arches.
Bituminous material shall be tested according to AASHTO M190. Original test data and calculations shall be recorded in Laboratory workbooks. Test results shall then be recorded through SiteManager.
1021.4.2 Sample Record
The sample record shall be completed in SiteManager, as described in Automation Sec 3510 and shall indicate acceptance, qualified acceptance or rejection. Appropriate remarks, as described in 106.9 Reporting Test Results, are to be included in the remarks to clarify conditions of acceptance or rejection. Test results shall be reported on the appropriate templates under the Tests tab.